Sleek SNS Emergency Lights are designed for reliable performance, helping you maintain compliance with NFPA 101 and local fire code regulations. Feature durable, lightweight thermoplastic construction with adjustable, high-output lamps to deliver bright illumination during emergencies.
SNS Emergency Lights allow you to automate your testing process to ensure you have reliable lighting throughout your facility in the event of an emergency. Designed to integrate seamlessly with the Primex Wireless Synchronous Network System (SNS), Emergency Lights communicate via your existing 802.11 b/g wireless or Ethernet network to allow you to fully automate your emergency light testing process for NFPA 101 compliance. Using the Web-based SNS Applications Management Platform (AMP) interface, facility managers can run automated periodic and annual tests of lamps and batteries, log performance and provide reports as needed. Service and repairs can be proactively scheduled to minimize disruption to building occupants, maximize safety and maintain compliance with NFPA 101 requirements.
Durable Construction for Long Life
All models feature durable, lightweight thermoplastic construction with
adjustable, high-output lamps to deliver bright illumination during
Emergency Light Features
Durable white thermoplastic housing
For new installations or replacement of existing emergency lights
802.11 b/g Wireless or Ethernet communication
Test, report and archive performance using SNS AMP software
Emergency Light Specifications
White injection-molded thermoplastic ABS housing is impact, corrosion and flame resistant (UL 94V-0 Flame rating)
Measures 12.125″W x 9.125″H x 4.125″D (30.8cmW x 23.1cmH x 10.5cmD)
Mounts on Wall or Ceiling
2 x 6V 5.4W Halogen MR-16 bulbs
Two emergency light heads are fully adjustable to direct light appropriately
120/277 VAC dual voltage units
Manual override test button and LED monitor allows manual periodic and annual testing, calibration and status readings
6V 4.5Ah lead-acid battery delivers more than 90 minutes of emergency light
Requires 24 hours to recharge after a 90-minute discharge
Low voltage battery disconnection to avoid excessive discharge
802.11 b/g Wireless or Ethernet communication.
Security Encryption: WEP, WPA, WPA2
Authentication: LEAP, EAP-FAST, PEAP